That moment when you realize that your facility's electrical power has shut down, thus slowing down operation at your parking garage for a period of time. This issue may give off the wrong idea to potential customers and you could lose income temporarily. Be prepared for a future power outage by installing the Bodine brand electronic ballast.
Our B4CF2P Cold-Pak model will provide emergency power to your lighting system even if it's in a damp or wet location. A sealed nickel cadmium (NiCad) battery will automatically provide a temporary lighting source for up to 90 minutes once power fails. Composed of electrical steel, this ballast can be used either indoors or outdoors.
Operates: one or two CFL/T5 Circline lamp units
Backup time: 90 minutes
Primary Light Output: Up to 925
Dual Operating Voltages: 120/277V
AC Operating Power Rating: 15 Watts
Test Switch: Single Pole
Recharge Time: 36 Hours
The B4CF2P Cold-Pak can be installed on top, inside of, or remotely to a CFL fixture with a conduit (included). Remote installation is recommended at a maximum of 6 feet in distance from lamp. For simple visual check up of the charging indicator light and for easy testing, the test/monitor plate can be installed near the fixture.
It can be used either with switched or unswitched mode of fixture. If a switched fixture is used, an unswitched live wire must be connected to the emergency ballast for feeding the emergency ballast through AC circuit. The B4CF2P Cold-Pak can be installed inside or on top of the fixture.
Input power for B4CF2P Cold-Pak is 15W with a battery capacity is 19.2 Watt-hour, which meets emergency standards, set out by the National Electrical Code (NEC). This emergency ballast also has delay timer of 3 seconds to prevent under voltage false tripping. It can operate more than one (1) compact fluorescent lamp depending upon the wattage at 910 lumens. Its backup time is 90 minutes in emergency mode.
National Electrical Code (NEC)
Life Safety Code (NFPA-LSC)
Weight: 3 lbs